|Compatible Batteries||Encapsulated Lead Batteries|
|Wind Generator System||Voltage||24V|
|Capacity||200Ah or greater|
|Solar Panel||Input Voltage||0-50V|
|Safety Mechanisms||Overcharge Protection Engages||30V|
|Overcharge Protection Releases||26.2V|
|Electromagnetic Brake I||Overcharge Protection|
|Electromagnetic Brake II||Excess Generation Protection|
|Manual Brake Switch||ON/OFF|
|Stand-By Power Consumption||0W|
Our hybrid controller unit can accommodate a photovoltaic system of up to 210W in addition to the C1000TH, our 1kW turbine model..
Safe operation is virtually guaranteed by several features which prevent charging problems, control rotation speed and allow manual stops for maintance.
Once the battery charge exceeds 30V the brake will engage and solar power will be limited, the system enters the float charge mode. Normal operation will resume when the battery charge drops back below 26.2V.
- Overgeneration Protection
If overheating occurs, the braking system slows down the blade rotation speed, permitting for cooling and automatic recovery.
- Manual Brake
The manual brake switch will stop the wind turbine's rotation for routine maintenance or during emergencies.
* Caution: Do not egage the manual brake if blades are rotating at high speeds. Damage to the turbine might orccur.
Please see the illustrations below for setup examples in a hybrid wind and solar configuration. Or check out photos of our wind turbine installations and applications in various countries. For International examples please click HERE. International examples can be browsed by country or setup type. Domestic examples can be accessed by provinces from HERE.